Not getting heat and noticing error code 228 from your Lennox® furnace?
This shows your HVAC equipment couldn’t regulate its pressure switch before turning on. As a result, your system will not run for safety reasons.
Repairing or replacing this part is better left to the Experts at Air Engineers Service Experts in Jacksonville. Our NATE-certified technicians are among the elite in the industry. They’re well-qualified to work on all of your heating needs, including fixing a furnace error.
We want you to be absolutely satisfied with our quality furnace repair in Jacksonville. That’s why we back it with a 100% Satisfaction Guarantee* for a year.
How a Pressure Switch Works
This part plays a critical part as your furnace prepares to heat your space.
Here’s what occurs after your thermostat’s call for heat:
- Your furnace’s control board starts running the draft inducer blower motor. This exhausts combustion gases from the heat exchanger and moves in new gas and air so the burners can fire.
- When the pressure switch senses that enough air is being pulled into the burners, it closes and commands the control board to ignite the furnace.
- Your furnace ignites and creates heat.
What Happens When a Pressure Switch Breaks Down
When your pressure switch isn’t working promptly, you’ll likely hear the fan going and the switch clicking a few times before the furnace switches off completely. When a part isn’t functioning right, your furnace will turn off to protect you.
Your furnace will let you know something is amiss with a red flash from its indicator light, which it uses to exhibit error codes. It uses this red light to flash code, like Morse code.
You may notice fast flashes or an alternating slow flash as it passes on a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Air Engineers Service Experts tech will check other parts of your furnace first. Several other issues can also create the error code, like a blocked vent or cracked hose.
The bill to repair your furnace depends on the issue with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can expect to pay between $40 to $350.
Count on the Experts at Air Engineers Service Experts
If you need furnace repair, turn to the pros from Air Engineers Service Experts to check out the fault code and fix the issue to your requirements.
Call us at 904-450-5672 or schedule an appointment online today.